This section is designed on the basis of:
- SNIP 41-02-2003 "HVAC".
- The customer's specifications.
- Building and technological parts of the project.
This section is provided an apparatus heating and ventilation systems in the premises parking lot in a residential area "Gayva" Perm.
The room is provided for storage of cars without heating.
Heating domestic premises car park (the guards room and toilet room) is satisfied
using electric heaters factory manufacturing company NOBO model Nordic C4E10, C4E15 and C4E20.
The parking spaces provided for supply and exhaust ventilation with mechanical drive,
and smoke ventilation. Ventilation systems are separate for each floor parking.
Ventilation basement accomplished with supply air (P1) and exhaust systems (B1, B3)
P1 system is designed to supply air into the room parking lot at around minus 3,300 meters.
B1 system is designed to remove air from the room parking lot at around minus 3,300 meters.
B3 System is designed to remove air from the room bathroom.
Ventilation of the first floor done using fresh air (P2) and exhaust systems (B2)
P2 system is designed to supply air into the room parking lot at around 0,000 m.
B2 system is designed to remove air from the room parking lot at around 0,000 m.
Hop metal ducts are designed with a coating that provides fire resistance of 1 hour. At the intersections with fire barriers ducts equipped with flame-retardant valves with the same fire-resistance rating.
Emissions of exhaust air exhaust systems to organize at a height of not less than 1.0 meters from the roof of the building
and not closer than 10 meters to the air intake device.